Here is the abstract you requested from the HITEN_2017 technical program page. This is the original abstract submitted by the author. Any changes to the technical content of the final manuscript published by IMAPS or the presentation that is given during the event is done by the author, not IMAPS.
|An Advanced Extreme Environment Wireless Telemetry System for Turbine Blade Instrumentation|
|Keywords: Wireless, Telemetry, SiC|
|As advanced natural gas power generation systems evolve, the thrust for increased efficiencies and reduced emissions results in increasingly harsh conditions inside the turbine environment. These high temperatures, pressures, and corrosive atmospheres result in accelerated rates of degradation, leading to failure of turbine materials and components. Wolfspeed, A Cree Company, Siemens Energy and Siemens Corporate Technology, in collaboration with the DoE’s National Energy Technology Laboratory (NETL), are developing a reliable and long-term monitoring capability in the turbine hot gas path in the form of novel ceramic based thermocouples and wide band gap instrumentation electronics that will contribute to the overall reliability of gas turbines. When equipped with better monitoring and controls, power plants can operate with increased fuel-burning efficiency, improved process dynamics and gas concentrations, and increased overall longevity of the power plant components. This will result in increased turbine availability and a reduction in outages and maintenance costs. The technology being developed in this program is based upon advanced techniques and innovations in nearly every aspect of high temperature electronics, including materials, subcomponents, semiconductors, electronic packaging, and system integration. The environment in which this wireless system must operate has continuous g-loads on the order of 16,000g, and temperatures exceeding 400 ºC. This paper will specifically discuss the background and motivation for the high temperature instrumentation system, and will explain the high-level electrical system, the construction of the instrumentation package, the techniques utilized for integration onto rotating components, as well as the wireless power and data transmission systems. In addition to the electrical and mechanical design, this paper will also discuss results from laboratory bench testing as well as heated spin rig testing. Finally, this paper will highlight the future direction of the instrumentation system evolution, with a final objective of insertion into Siemens natural gas turbine power plants.|
|John R. Fraley, Development Engineering Manager
Wolfspeed, A Cree Company